Re: [new_distillers] safe circuit

Expand Messages
• Hi Luke, Knowing the country and even the state you are in and the voltage of the circuit you have would help a lot but here we go. Is the 30 amp fuse the
Message 1 of 5 , Dec 27, 2005
Hi Luke,

Knowing the country and even the state you are in and the voltage of the
circuit you have would help a lot but here we go.
Is the 30 amp fuse the original (the size fuse that the circuit has always
had and was designed to have)? Is the wiring all in good condition? If so
all you have to do is multiply the voltage of the circuit by the amp rating
of the fuse to find the wattage capacity.
Eg. 240 x 30 = 7200 watts (240 volts it the Australian standard check the
even a standard 10amp circuit at 240 volts should handle 2400watts.
As long as you keep your usage atleast 10% below this you should be safe.
Now having said that IF your not sure of the original fuse size have the
circuit checked.

Remember electricity kills, if you can't be sure dont do it it's just not
worth it.
Dean.

> I have about 1840w running threw about 20 feet of 12 an 14 gauge wire.
> There is also an over head garage light on that circuit. there is a 30
> amp fuse on the circuit, my question is, is this a safe set up?
>
> thanks
> Luke
• In a word, NO. Where I am, 14 ga.wire would have no more than a 15 amp fuse, and 12 ga. a 20 amp. At 110 volts, you re running 16.8 amps (not to mention the
Message 2 of 5 , Dec 28, 2005
In a word, NO.
Where I am, 14 ga.wire would have no more than a 15 amp fuse, and 12
ga. a 20 amp. At 110 volts, you're running 16.8 amps (not to mention
the light). JMSO
Tip one, Fireball Morgan

--- In new_distillers@yahoogroups.com, "enibnikrib" <manson@i...> wrote:
>
> I have about 1840w running threw about 20 feet of 12 an 14 gauge wire.
> There is also an over head garage light on that circuit. there is a 30
> amp fuse on the circuit, my question is, is this a safe set up?
>
> thanks
> Luke
>
• ... Hi Morgan I changed the fuse to 20 amp. that box is full of 30 amp. fuses. They have been there since I have owned the house, about 20 years. Guess I gotta
Message 3 of 5 , Dec 29, 2005
--- In new_distillers@yahoogroups.com, "morganfield1"
<morganfield1@y...> wrote:
>
> In a word, NO.
> Where I am, 14 ga.wire would have no more than a 15 amp fuse, and 12
> ga. a 20 amp. At 110 volts, you're running 16.8 amps (not to mention
> the light). JMSO
> Tip one, Fireball Morgan
>
> --- In new_distillers@yahoogroups.com, "enibnikrib" <manson@i...> wrote:
> >
> > I have about 1840w running threw about 20 feet of 12 an 14 gauge wire.
> > There is also an over head garage light on that circuit. there is a 30
> > amp fuse on the circuit, my question is, is this a safe set up?
> >
> > thanks
> > Luke
> >
>
Hi Morgan

I changed the fuse to 20 amp. that box is full of 30 amp. fuses. They
have been there since I have owned the house, about 20 years. Guess I
gotta get another power strip because this one is rated at 15 amp. I
thought I would put each element on seperate power strips. The
florescent light still dims, nobody can figure that one out. There is
no power drop. I feel a little safer with the lower amp. fuses.

thanks

Luke
Your message has been successfully submitted and would be delivered to recipients shortly.