49171Re: permitting questions
- Apr 9, 2013My understanding is the pile height limits for storage still apply; the IFC chapter 34 exemption for barrels and bottles only counts toward reducing your MAQ. Hence, the storage height for all bottles and barrels needs to be kept under 6'.I guess it's up to your local FD as to what they are comfortable with and how they interpret the code. As long as you store <120 gal of feints in tanks, and everything else is "in-process", you could argue you don't need to comply with all the H-3 requirements, but they may not agree.Best of luck and let us know how it goes.
- << Previous post in topic